Optionally, you can also connect the inverters to each other with a network cable.
e.manager terminal A <=> Danfoss WR terminal RX/TX B(+)
e.manager terminal B <=> Danfoss WR terminal RX/TX A(-)
UnixLynx inverters do not require any settings to be made.
Please proceed as follows for each inverter:
And enter the password 1761. The display shows "Security level: 1".
Please enter the following:
- Network: 1
- Subnet: 1
- Address: X
Please enter a unique address here.
For TripleLynx inverters, the address must be between 1-50.
Restarting the inverter
To ensure that all parameters are safely adopted, please restart the inverter (switch off the voltage on the AC and DC sides for at least five minutes).